- Solenoid operated pilot valve and burner valve
by normal control or through remote handset for flame ignition.
- Diaphragm-operated second automatic valve opens under
control of regulator; closes if gas or power supply is interrupted.
- Fixed pressure regulator for ON-OFF operation
or Stepping Motor Pressure Regulator.
- Pilot outlet flow adjustment
- Burner outlet pressure adjustment
- Outlet Pressure Adjustment Range:
NG 1"~4" W.C. / LPG 4"~10" W.C.
- Maximum Inlet Pressure: 35 mbar
- Flow Capacity (1" W.C. Pressure Drop):
NG: 50,000 BTU/hr / LPG: 80,000 BTU/hr
- Operating Temperature: -23°C~80°C